Prefabricated European Box Type Substation/Power Distribution Transmission/Station
|FOB Price:||US $500 / Set|
|Min. Order:||1 Set|
|Min. Order||FOB Price|
|1 Set||US $500/ Set|
|Transport Package:||Seaworthy Packing|
|Payment Terms:||L/C, T/T, D/P, Western Union|
- Model NO.: YBW -12
- Certification: ISO9001, ISO14001, Ohsas18001, 3c, TUV, Ce
- Operation Voltage: High Voltage
- Brand: Gse
- Origin: China
- Structure: Protection
- Form: All- Packaged Type
- Shell Material: Wooden
- Trademark: GSE
prefabricated European box type substation/power distribution transmission/station
1,The base plane should be reinforced;
2,The number and orientation of the embedded steel pipe in the foundation are determined by the user according to the number of cables and the orientation of the cable;
3,Cable should stand in the basic fixed, embedded iron and support should be grounded;
4,The number of ground rods shall be determined by the soil condition, and the grounding resistance should be less than 4Q;
5,The grounding electrode and the ground wire connection must be welded with brush asphalt anti-corrosion;
6,The location of the steps of the user according to the box to open the door of the location of custom; (refer to layout)
7,Try to determine the pit and other dimensions of visual installation conditions;
8,Based on reference only, the user can modify according to the actual situation.
Installation and maintenance
Intelligent integrated substation in installation, acceptance, handover test, operation and maintenance, etc.
The electricity sector requires the implementation of the provisions, but also pay attention to the following matters.
1,When the user receives the goods should be in accordance with the relevant provisions of the inspection, for not immediately installed products, should be in accordance with the normal conditions of use, stored in the appropriate place,
2,The product should adopt the special sling bottom lifting.
3,The level of products placed in advance of the foundation, then the gap between the base and the base of the products with cement mortar sealing, hair free of rain water into the cable compartment, through the high and low pressure chamber of the bottom seal board is connected with the high and low voltage cable.
4,The product after installation should be reliable grounding, power plant base on channel two main earthing terminal, transformer neutral point arrester and the shell, under the pile head shall be installed separately by the Department of grounding and grounding should all share a grounding device, should be less than 4 ohm based grounding resistance, grounding from this product is led to the grounding wire should be less than 2.
5,The product is installed or repaired, the following items were put into operation before the inspection and test should be;
(1)Will be able to clean up the power station; (2)Flexible operating mechanism;
(3)The main electrical equipment is flexible and reliable; (4)The electrical auxiliary contact is reliable;
(5)Meter and relay action is accurate; (6)The change of the instrument and the transformer and the polarity of the wiring is correct;
(7)All electrical installation nut is screwed, installation is firm and reliable;
(8)The bus connection is good, the base support insulator, the clamp is the reliable installation;
(9)The original sketch value of whether it meets the requirements, whether the fuse core is correct;
(10)The main circuit and auxiliary circuit is in line with the requirements of the electrical schematic diagram.
(1)All components of the product are maintained according to their respective technical requirements;
(2)If the transformer used for oil immersed type, should be at least once a year according to the specifications of the sampling analysis and inspection;
(3)In the operation of the high voltage side switch equipment, after 20 times of load or 2000 times no load switch operation, should check the contact condition and the loss degree of arc extinguishing device, found abnormal should be in repair or replacement.
(4)The reason for the automatic tripping of low voltage switch equipment can be put into operation after the fault is eliminated;
(5)Arrester year should be a pre test before the thunderstorm season; products with the packing list, certificate, installationmanual, electrical wiring ring and the products used by the main components of the equipment specifications, key operating tools and spare parts according to the agreement provided.
It is one of the most professional and famous expertise in North China. With major business of power distribution equipment, power transformer euipment, box-type substation, electricity measuring and high-voltage metering device, as well as the power device, instruments&meters, measuring box with GRP and PC+ABS material, charging equipment for electric car, photovoltaic power generation(without generator set) and wind power generation equipment both in producing and selling. For a 3C authentication factory by nationality and already got the ISO9001 quality management system, OHSAS18001 occupation health and safety management system and ISO14001 environment certification.
1, The most favorable offer from professional factory with assurance quality for you!
2, Cooperate with the State Grid Corporation of China many years!
3, All your question will be kindly feedback in 24 hours all the time!
4, No MQQ limit and all the related certification is available!
5, We promised that more profit and pleasure will be got once business relationship established between us!
6, Welcome to visit our factory and your precious advise is expecting forever!
Shandong Yangxin Genshen Electric Co., Ltd.
Qingdao Yaoutongxing International Trading Co., Ltd.(subsidiary)
Attn: David (sales manager)
Ph: 0086-136 5865 3423
Add: Zhoushang Development Zone,Yangxin Binzhou city, China.
Room 2202, Longhaimingzhu Mansion, Laoshan District, Qingdao city China.